For use in a closed loop design. Flow up to 2200 L/h (9.7 USgpm).
In conjunction with boilers having high resistance (condensing) or when total flow rate of all parallel running circulators is higher than maximum flow rate of the boiler, the low-loss header provides hydraulic separation, decoupling boiler and system circuits from each other.
It is recommended to use the low-loss header in applications in which the total system flow rate exceeds the maximum boiler flow rate. PAW strongly recommends the use of a hydraulic separator in cases where the system head and flow rates are unknown.
Our Solar Thermal Newsletter!
FREE tips on Making Sales, Technology Guides & More! | Archive
777 Warden Ave. Store #6, Toronto, Ontario, M1L4C3 Canada